LSS steam boiler introduction
.采用弯水管偏置式结构，由燃烧器喷出的高温火焰首先冲刷炉胆烟管，然后由后回转烟室进入由弯水管组成的二次回程，经烟囱排入大气。 0.3 ton 0.5 ton 0.7 ton 1 ton 7 kg pressure vertical fuel gas burning methanol liquefied gas steam boiler . Adopting a bent pipe offset structure, the high-temperature flame sprayed from the burner first flushes the furnace bile flue, and then turns the smoke back The chamber enters a secondary return consisting of bent water pipes and is discharged into the atmosphere through the chimney. The boiler is equipped with a removable mosaic structure, which makes the boiler maintenance very convenient. The boiler is equipped with a technically good burner, which adopts advanced technologies such as automatic combustion proportional adjustment, automatic feed water adjustment, program start and stop, and fully automatic operation, and has automatic protection functions such as high and low water level alarms, extremely low water levels, super high steam pressure, and flameout. . This type of boiler has the characteristics of compact structure, safety and reliability, easy operation, rapid installation, less pollution, low noise, high efficiency and so on.
Pay attention to the following points during operation of oil-fired gas boilers:
1. No positive pressure combustion or furnace smoke spray is allowed.
2. No water can accumulate on the ground plane of the bottom of the oil-fired gas boiler to prevent moisture and corrosion.
3. The boiler operation should be inspected every 2-3 weeks.
4. After every 3-6 months of boiler operation, the boiler should be stopped for comprehensive inspection and maintenance.
(1) Check the inside and outside of the boiler, such as the welds in the pressured part, whether there is corrosion inside or outside the steel plate. If serious defects are found, they should be repaired in a timely manner. When it is suspicious but does not affect safety, records should be made for future reference.
(2) Boiler primer can be applied to the water surface after inspection to prevent corrosion.
5. Paint the boiler and boiler base at least once a year.
6, fuel gas boilers are not used regularly maintenance methods: dry and wet methods, the furnace should be stopped for more than one month, dry maintenance method should be adopted, the furnace can be used for less than one month after the wet maintenance method.
Technical parameters of LSS vertical fuel steam boiler:
| model || LSS-0.3-0.7-YQ || LSS-0.5-0.7-YQ || LSS-0.7-0.7-YQ || LSS-1-0.7-YQ |
| Evaporation || 0.3 || 0.5 || 0.7 || 1.0 |
| Fixed work stress || 0.4 / 0.7 || 0.4 / 0.7 || 0.4 / 0.7 || 0.4 / 0.7 / 1.0 |
| Steam saturation temperature || 151/170 ||
151/170 || 151/170 || 151/170/184 |
| Use fuel || Diesel || Diesel || Diesel || Diesel |
| Thermal efficiency || 92.6% || 93.2% || 93.6% || 93.8% |
| Fuel consumption || 20/14 || 35/29 || 42/38 || 70/61 |
| Dimensions || 1.2x2.6 || 1.4x3.1 || 1.6x3.2 || 1.8x3.4 |