Henan Taiguo Boiler Manufacturing Co., Ltd.
(Former Henan Taikang Boiler Factory)
Consulting Hotline: 137-3387-8722
Official Website: http://ibgraffix.com/
Address: Taikang County Industrial Park, Henan Province
2059045363 QQ Online: 2059045363
LSS type fuel gas boiler is a vertical internal combustion bent water tube boiler. The bent pipe offset structure is adopted. The high-temperature flame sprayed from the burner first flushes the furnace bile pipe, and then enters the second return journey consisting of the bent pipe from the rear rotating smoke chamber, and is discharged into the atmosphere through the chimney. The boiler is equipped with a removable mosaic structure, which makes the boiler maintenance very convenient. The boiler is equipped with a technically good burner, which adopts advanced technologies such as automatic combustion proportional adjustment, automatic feed water adjustment, program start and stop, and fully automatic operation. . This type of boiler has the characteristics of compact structure, safety and reliability, easy operation, rapid installation, less pollution, low noise, high efficiency and so on.
1. Pay attention to the following points during operation of oil-fired gas boilers:
(1) No positive pressure combustion or furnace smoke is allowed.
(2) Water should not accumulate on the ground plane of the bottom of the oil-fired gas boiler to prevent moisture and corrosion.
2. The boiler should be inspected every 2-3 weeks.
3. After every 3-6 months of boiler operation, the boiler should be stopped for comprehensive inspection and maintenance.
(1) Check the inside and outside of the boiler, such as the welds in the pressured part, whether there is corrosion inside and outside the steel plate. If serious defects are found, they should be repaired in time. If the defects are not serious, they will be repaired at the next shutdown. When it is suspicious but does not affect safety, records should be made for future reference.
(2) Boiler primer can be applied to the water surface after inspection to prevent corrosion.
4. Paint the boiler and boiler base at least once a year.
5. Maintenance methods for oil and gas boilers that are not used regularly: There are two methods, dry and wet. If the furnace is stopped for more than one month, dry maintenance should be adopted. If the furnace is stopped for less than one month, wet maintenance can be used.
(1) After the fuel gas boiler is stopped, remove the boiler water, completely remove the internal dirt, and dry it with a low fire (be careful not to have a large fire), then install a 10-30 mm block of quicklime and place it in the furnace tube. , Do not make quicklime contact with metal, the weight of quicklime is calculated according to the drum volume of 8 kg per cubic meter. Then close the head hole, hand hole, pipeline valve, check every three months, if the quicklime is broken into powder, you must When the fuel oil gas boiler is replaced, the quicklime and the tray are taken out.
Oil-fired gas boilers are required to operate when the boiler water temperature / pressure is normal and the water supply is stable. Keep the boiler room clean. Do a good job of shift work. Give full play to human factors. Strengthen the observation of various mechanical equipment and instruments. To ensure safety and reliability, prevent accidents, and pay attention to saving fuel, the boiler operator should regularly sum up experience and continuously improve the operation level.
The boiler room is clean and tidy with bright lights. Boilers and accessories (including pipes, valves, meters) are safe, sensitive and reliable.
The two parties in the handover team must make the handover thoroughly and earnestly, and record the situation and problems in the handover in the operation record book.
1. Feedwater requirements: The boiler feedwater is best treated by chemical treatment outside the boiler. The water quality should meet the requirements of GB 1576-2001 "Industrial boiler water quality", and the total hardness of the feedwater is not more than 0.03mmol / L. See the boiler water quality requirements for specific regulations.
2. Water supply equipment: Whether the running water supply pump is normal or not should be inspected by driving during shift work, and repaired immediately if there is a fault.
Generally, the feedwater contains more or less minerals. After the feedwater enters the boiler to be gasified, the minerals remain in the boiler. After concentrating to a certain extent, the minerals settle down in the boiler. With a large amount of evaporation and a long running time, there are many deposits. The quality of the feed water must be guaranteed. The alkalinity of the boiler water should not exceed 1.25 milligram equivalents / liter. When it exceeds the above range, the boiler water should be discharged. When the test conditions are not complete, ordinary users regularly discharge sewage according to specific conditions, such as once a day or once per shift.
1. The cold furnace starts quickly and achieves high temperature and pressure in a short time;
2, natural circulation, can withstand large temperature differences
3. It has multiple chain protections such as water level and steam pressure.
4.The vertical structure is compact and beautiful, elegant in shape, bright in color, small in area and easy to install;